Where is the broken bridge aluminum non-insulated fire window used? Where to use broken bridge aluminum non-insulated fire windows?
根据 2015 年 5 月 1 日实施的 GB50016-2014 《建筑设计防火规范》中 5.5.32 建筑高度大于 54m 的住宅建筑，每户应有一间房间符合下列规定： 1. According to GB50016-2014 "Code for Fire Protection in Building Design" implemented on May 1, 2015 , 5.5.32 residential buildings with a building height greater than 54m , each house should have a room that meets the following requirements:
、应靠外墙设置，并应设置可开启外窗； (1) It shall be set up against the external wall and shall be provided with an openable window;
、内、外墙体的耐火极限不应低于 1.00h ，该房间的门宜采用乙级防火门，外窗宜采用耐火完整性不低于 1.00h 的防火窗 ; (2) The fire resistance of the inner and outer walls should not be less than 1.00h . The door of the room should be a class B fire door, and the outer window should be a fire window with a fire integrity of not less than 1.00h ;
《建筑设计防火规范》中 6.7.7 除本规范第 6.7.3 调规定的情况下，当建筑的外墙外保温系统按本规范第 6.7 节规定采用燃烧性能为 B1 、 B2 级的保温材料时，应符合下列规定： 2. In GB50016-2014 "Code for Fire Protection of Building Design" 6.7.7 Except for the regulation in Section 6.7.3 of this code , when the external insulation system of the building adopts the combustion performance of B1 and B2 according to section 6.7 of this code Grade insulation materials shall meet the following requirements:
除采用 B1 级保温材料且建筑高度不大于 24m 的公共建筑或采用 B1 级保温材料且建筑高度不大于 27m 的住宅建筑外，建筑外墙上门、窗的耐火完整性不应低于 0.50h 。 Except for public buildings using Class B1 insulation materials and building heights of no more than 24m or residential buildings using Class B1 insulation materials and building heights of not more than 27m , the fire integrity of doors and windows on the exterior walls of buildings should not be less than 0.50h .
断桥铝非隔热防火窗可以用钢质或者塑钢的非隔热窗代替吗？ Previous: Can the non-insulated fire windows of broken bridges be replaced by non-insulated windows made of steel or plastic? 断桥铝非隔热防火窗属于3C产品吗？ Next: Is a broken bridge aluminum non-insulated fire window a 3C product? Is there a maximum size and division limit?