Code for fire protection design of building interior decoration
The safety protection measures during the decoration process are important safety factors. You cannot simply renovate for the sake of decoration and ignore the fire protection and fire protection design during the decoration process. The fire protection code for the interior decoration design of the building clarifies the fire protection design requirements that should be followed during the decoration process. And others' safety.
总则 1 General
为保障建筑内部装修的消防安全 , 贯彻 “ 预防为主、防消结合 ” 的消防工作方针 , 防止和减少建筑物火灾的危害，特制定本规范。 1.0.1 In order to ensure the fire safety of the interior decoration of the building , implement the fire prevention work policy of " prevention-oriented and combination of prevention and elimination " , and prevent and reduce building fire hazards, this code is specially formulated.
本规范适用于民用建筑和工业厂房的内部装修设计。 1.0.2 This code applies to the interior decoration design of civil buildings and industrial plants. This code does not apply to the interior decoration design of ancient buildings and wooden structures.
建筑内部装修设计应妥善处理装修效果和使用安全的矛盾，积极采用不燃性材料和难燃性材料，尽量避免采用在燃烧时产生大量浓烟或有毒气体的材料，做到安全适用，技术先进，经济合理。 1.0.3 The interior decoration design of the building should properly handle the contradiction between the decoration effect and the safety of use. Actively adopt non-combustible materials and non-combustible materials, and try to avoid using materials that generate a large amount of dense smoke or toxic gases during combustion, and be safe and applicable. Advanced technology and reasonable economy.
(1) 隔断系指不到顶的隔断。 Note: (1) Partition refers to sub-top partitions. The fixed partition decoration to the top shall be the same as the wall regulations;
柱面的装修应与墙面的规定相同。 (2) The decoration of the cylindrical surface should be the same as that of the wall surface.
兼有空间分隔功能的到顶橱柜应认定为固定家具。 (3) The top-to-top cabinet with space separation function shall be identified as fixed furniture.
建筑内部装修设计，除执行本规范的规定外，尚应符合现行的有关国家标准、规范的规定。 1.0.5 In addition to the implementation of the provisions of this code, the interior decoration design of the building shall also comply with the current relevant national standards and specifications.
装修材料的分类和分级 2 Classification and classification of decoration materials
装修材料按其使用部位和功能，可划分为顶棚装修材料、墙面装修材料、地面装修材料、隔断装修材料、固定家具、装饰织物、其他装饰材料七类。 2.0.1 Decoration materials can be divided into seven categories: ceiling decoration materials, wall decoration materials, floor decoration materials, partition decoration materials, fixed furniture, decorative fabrics, and other decorative materials.
(1) 装饰织物系指窗帘、帷幕、床罩、家具包布等； Note: (1) Decorative fabrics refer to curtains, curtains, bedspreads, furniture coverings, etc .;
其他装饰材料系指楼梯扶手、挂镜线、踢脚板、窗帘盒、暖气罩等。 (2) Other decorative materials refer to stair railings, mirror hanging lines, skirting boards, curtain boxes, heating covers, etc.
装修材料按其燃烧性能应划分为四级，并应符合表 2.0.2 的规定： 2.0.2 Decoration materials shall be divided into four levels according to their combustion performance, and shall meet the requirements of Table 2.0.2 :
Decoration material combustion performance grade table
Burning performance of decoration materials
装修材料的燃烧性能等级，应按本规范附录 A 的规定，由专业检测机构检测确定。 2.0.3 The combustion performance level of decoration materials shall be determined by professional testing institutions in accordance with the provisions of Appendix A of this code . 级装修材料可不进行检测。 B3 grade decoration materials may not be tested.
安装在钢龙骨上燃烧性能达到 B1 级的纸面石膏板，矿棉吸声板，可作为 A 级装修材料使用。 2.0.4 Installed on the steel keel, the paper surface gypsum board with B1 combustion performance and mineral wool sound absorption board can be used as A -grade decoration materials.
当胶合板表面涂覆一级饰面型防火涂料时，可做为 B1 级装修材料使用。 2.0.5 When the surface of plywood is coated with a first-grade decorative fireproof coating, it can be used as a B1 decoration material. B1 级。 When plywood is used for ceiling and wall decoration and does not contain objects such as electrical appliances, wires, etc., it is advisable to apply fire-resistant coating only on the outer surface of the plywood; The inner and outer surfaces of the plywood and the corresponding wooden keels shall be coated with fire-resistant coatings or shall be flame-resistant impregnated to B1 level.
Note: The grade of facing fire-resistant coatings shall comply with the relevant provisions of the current national standard "Test Methods and Classification Standards for Fire-resistant Performance of Fire-resistant Coatings".
单位重量小于 2.0.6 unit weight is less than
施涂于 A 级基材上的无机装饰涂料，可做为 A 级装修材料使用；施涂于 A 级基材上 , 湿涂覆比小于 2.0.7 Inorganic decorative coatings applied to A -class substrates can be used as A -class decoration materials; when applied to A -class substrates , the wet coating ratio is less than
当采用不同装修材料进行分层装修时，各层装修材料的燃烧性能等级均应符合本规范的规定。 2.0.8 When different decoration materials are used for layered decoration, the combustion performance level of each layer of decoration material shall meet the requirements of this specification. The composite decoration materials should be tested integrally by a professional testing agency and their combustion performance grades should be divided.
常用建筑内部装修材料燃烧性能等级划分，可按本规范附录 B 的举例确定。 2.0.9 The classification of the combustion performance grades of commonly used building interior decoration materials can be determined according to the examples in Appendix B of this code .
Details please download and view
Link: http://pan.baidu.com/s/1skLxL9r Password: 9n58
After clicking the download link, please enter the document extraction code: 9n58九安防火门产品检验报告3C证书明细表 Previous ： Detailed List of 3C Certificate of Jiu'an Fire Door Product Inspection Report 消防设计公司针对消防设计依据的消防设计管理规定 Next post: Fire design management regulations for fire design companies based on fire design basis